- FULL PAPER
- Open Access
Sensitivity of geomagnetically induced currents to varying auroral electrojet and conductivity models
- Ciarán D Beggan^{1}Email author
Received: 8 September 2014
Accepted: 6 December 2014
Published: 15 February 2015
Abstract
Geomagnetically induced currents (GIC) are created by the interaction of rapid changes in the magnitude of the magnetic field with the conductive subsurface of the Earth. The changing magnetic field induces electric currents, which are particularly strong along boundaries between regions of contrasting conductivity structure such as the land and sea. A technique known as the ‘thin-sheet approximation’ can be used to determine the electric field at the Earth’s surface, which in turn allows the calculation of GIC in the earthing connections of high-voltage nodes within a power grid. The thin-sheet approximation uses a spatially varying conductance over the region of interest on a 2D surface, combined with a 1D layered model of upper lithosphere conductance. We produce synthetic models of the auroral electrojet in different locations over the United Kingdom (UK) and investigate the effects of varying the 2D thin-sheet model. We assess different two-dimensional surface conductance models and vary the underlying 1D conductivity models to simulate the effects of resistant through to conductive lithosphere. With an advanced network model of high-voltage electrical distribution grid, we compute the expected GIC at each node in the system given the input surface electric fields from the various synthetic electrojets and conductivity models. We find that the electrojet location is the primary control on the size of GIC, with conductivity being a second-order effect in general, though it can be locally important.
Keywords
Background
Electric fields are generated in the ground during large space weather events primarily due to the induction effects of a changing magnetic field within a conductive medium (i.e. the subsurface). During geomagnetic variations, geomagnetically induced currents (GIC) can flow in certain types of grounded systems such as long pipelines and electrical distribution systems. These currents are usually harmless but high-voltage power systems can be vulnerable to GIC flow if they offer a low-resistance path for the currents compared to the ground itself (Boteler et al. 2013; Pirjola 2005; Viljanen and Pirjola 1994). The social and economic impacts of an extreme space weather event could potentially be very large if were to cause damage to power transmission networks (c.f. Radasky 2011; Schulte in den Bäumen et al. 2014), and hence, large GIC are of concern to network operators and civil government, amongst others (Cannon 2013; Thomson 2014).
Studies of past space weather events in the United Kingdom (UK), such as McKay (2003) and Turnbull (2010, 2011), have modelled the impacts on simplified versions of the high-voltage transmission system in the UK, using basic representations of the conductivity structure of the land and bathymetry of the offshore continental shelf (Beamish et al. 2002). These models were able to reproduce GIC values measured in Scotland during the October 2003 storm (Thomson et al. 2005). Measured GIC (three phases summed) in the UK during the October 2003 event reached a peak of 40 A in one high-voltage node.
More recently, Pulkkinen et al. (2012) developed scenarios of realistic electric field changes for a 100-year extreme event to aid network engineers and planners. These were applied to the high-voltage network of Virginia in the USA (see also Bernabeu 2013) and to a relatively simple model of the UK high-voltage network to compute the expected GIC. In these models, GIC of up to 300 A were found. A one-dimensional conductivity depth model was used giving a uniform electric field model; however, it is expected, in reality, that large-scale spatial variations would occur during a significant geomagnetic storm. Viljanen et al. (2014) have also produced a model of the European high-voltage network as part of the EURISGIC project (Viljanen 2011) from which they computed GIC of up to 100 A, again using a simple conductivity structure for the British Isles.
In order to increase the complexity of the geophysical and engineering layers, Beggan et al. (2013) investigated the use of a more sophisticated high-voltage electrical network model coupled to a more representative two dimensional surface conductance model, as developed by Beamish and White (2012). These improvements were applied to a set of reasonable ‘worst-case’ magnetic field change scenarios for the UK mainland, based on work from Thomson et al. (2011). Values of up to 460 A were modelled in one node for an extreme 200-year return event.
These large GIC values were generated with a fixed set of conductivity model parameters. Until now, there has been little investigation into the sensitivity of the GIC values to variation in the geophysical conductance models used to create them. Previously, extreme end-member states were chosen, and intermediary values were assumed to vary linearly. The aim of this study is to check if these assumptions are valid for the sophisticated models that are currently being employed. To do so, we examine the differences between GIC values that arise when different 2D surface conductance models are used and when the underlying 1D depth model is varied. In the next section, we outline the models used and the methodology for computing GIC.
Methods
Computing models of GIC
To compute GIC within an electrical network, three main components are required: (1) a model of the conductivity structure of the region; (2) spatial and temporal measurements of the magnetic field; and (3) information about the topology and electrical properties of the high-voltage network. As we are primarily interested in how the conductivity affects GIC, we focus initially on the details of the one-dimensional depth and two-dimensional surface conductance models, before describing the synthetic auroral electrojets and high-voltage network model.
Conductivity models
The diffusion length of the magnetic field into the subsurface (skin depth) is dependent on the conductivity of the local region and the time period (frequency) over which the change of the magnetic field occurs. The vertical distribution of the resistivity within the Earth’s crust, and the period considered, determine the size of the induced electric field. Deeper layers are more significant at long periods, while shallow layers have a stronger influence at short periods. The interaction of the external magnetic field with the conductive Earth can be approximated by thin-sheet modelling and the frequency (i.e. period) of the rate of change of the magnetic field, which relates to the penetration depth.
The first 2D model (termed the ‘Constant’ model) is a simple land-sea model (Figure 1A). The depth-integrated conductivity (i.e. conductance) of the land is set to 20 S, while the conductance of sea water is set to 600 S. The second model is based on the work of McKay (2003) and is called the ‘AMK2003’ model (Figure 1B). This model has a more sophisticated bathymetric representation around the shallow continental shelf using a uniform value of sea water conductivity (4 S/m). Most of the land area is set to 20 S, but conductivity information from long-period magnetotelluric studies of the region around southern Scotland and northern England is included in these areas (e.g. Banks et al. 1983).
In 2012, a new UK thin-sheet conductivity model (termed ‘BGS2012’) was derived from the analysis of the resistivity properties of bedrock materials based on the British Geological Survey (BGS) 1:625,000 geological map of the UK and Northern Ireland (Figure 1C). This model uses information obtained from airborne geophysical surveys across the UK to provide a lithological and geostatistical estimate for all the UK bedrock formations. The central moments of the distributions were found to range from 8 to 3,125 Ω m (Beamish 2012). Over the continental shelf and ocean, a more complex bathymetry map was used, leading to a maximum conductance of approximately 1,600 S for the deeper parts of the Atlantic ocean. Onshore, the conductance values are for a depth integration of 3 km. The map differs strongly from the AMK2003 in the region around southern Scotland and northern England, as it relates to the shallow subsurface response as inferred from aerial survey but is self-consistent across the UK.
In addition to the two-dimensional surface conductivity, the thin-sheet modelling code also requires a layered one-dimensional conductivity model at depth. We construct six representative models for the conductance of the upper crust across the UK and a seventh representing a homogeneous half-space. The models are based on measurements made by various groups in the UK from 1977 to 1996 (see Banks et al. 1996; McKay 2003, and references therein), though applied across the UK as a whole for the purposes of this study.
One-dimensional resistivity models: 0 to 30 km [units: Ω m]
Depth (km) | 0 to 10 | 10 to 20 | 20 to 30 |
---|---|---|---|
Northern Highlands (NH) | 10,000 | 5,000 | 2,000 |
Central Highlands (CH) | 1,000 | 1,000 | 200 |
Midland Valley (MV) | 100 | 150 | 250 |
Southern Uplands (SU) | 20 | 20 | 1,000 |
Concealed Caledonides (CC) | 500 | 2,000 | 500 |
General Model (GM) | 1,000 | 1,000 | 500 |
Homogeneous half-space (HH) | 900 | 900 | 900 |
One-dimensional resistivity models: 30 to 390 km [units: Ω m]
Depth (km) | All models | Homog. Halfsp. |
---|---|---|
30 to 40 | 112.4 | 900 |
40 to 50 | 100.0 | 900 |
50 to 60 | 89.3 | 900 |
60 to 70 | 82.3 | 900 |
70 to 80 | 79.4 | 900 |
80 to 90 | 70.9 | 900 |
90 to 190 | 63.3 | 900 |
190 to 290 | 50.0 | 900 |
290 to 390 | 31.3 | 900 |
In terms of geological settings, the Northern Highlands model represents a very resistive terrane, found in northern Scotland, where the underlying lithology consists of granitic or metamorphic rocks. The Central Highlands are a less resistive version of this model. The Southern Uplands has a very conductive upper lithosphere, while the General Model is an intermediary between these end-member regions. The other models types examine the effect of a hidden resistive layer (Concealed Caledonides) or a more typical sedimentary basin setting (Midland Valley), common across the central and southern UK. The homogeneous half-space is a simple 1D moderately resistive model. Note that combining the three 2D surface models combined with the seven 1D depth models gives 21 different conductivity scenarios to assess.
Magnetic field models
To simulate the magnetic field during a geomagnetic storm, we created a series of representations of the magnetic field arising from a synthetic electrojet current system moving across the UK as the auroral oval expands southward. We constructed four simulated ‘electrojet’ models, all approximately 800 km wide, with a tapered-cosine form. Three of the models have an orientation approximately geomagnetically east-west aligned across the UK, placed at three different latitudes. The first lies over northern UK (‘northern Scotland’), the second over the central UK (‘northern England’) and the third along the southern coast (passing through ‘London’). For completeness, an orthogonal magnetic field direction in a geomagnetic north-south alignment (approximately following the central axis of the ‘Irish Sea’) was also created. Although such an orientation is not realistic due to the configuration of the main magnetic field, storms can exhibit a locally strong north-south component for short periods. The electrojet models were created as normalized values on a grid in geomagnetic coordinates and then rotated 10° counterclockwise to match the appropriate position over the UK in geographical coordinates. The electrojet grids were cropped and subsampled to 1/12th of a degree (≈ 10 km) to match the grid spacing of the 2D thin-sheet conductivity models.
We mimic the expected 30-, 100- and 200-year extreme scenarios of the magnetic field (c.f. Beggan et al. 2013), by scaling the electrojet H _{0} to 250, 320 and 450 nT for a period (T) of 2 min and 1,250, 1,575 and 2,275 nT for a period (T) of 10 min, giving six different magnetic field strength models. The values are chosen from the work of Thomson et al. (2011) based on records from European observatories over the past 30 years. Note that these are only meant to be snapshots of the extreme rate of change - such values are generally not sustained for very long (e.g. tens of seconds).
As there are four electrojet positions with six variations of field strength, this gives 24 different electrojet models. Together with the 21 different combinations of conductivity models, this gives a total of 504 different electric field models that can be computed.
Computing GIC
The values of V _{ ij } are the geo-voltages between nodes i and j computed from the electric field map with R _{ ij } being the line resistance between the two nodes, taken from the network model. The network parameters are also used to calculate Y and Z, and the geo-voltage is calculated by interpolating the electric field model values onto the positions of the transmission lines and integrating along a straight line between nodes. The GIC at each node on the grid is then computed using both the North and East components of the surface electric field. The vector I contains the estimated GIC for each node.
Results
Once the various electrojet and conductivity models were defined, we ran the thin-sheet modelling code for all 504 combinations of electrojet and conductivity model scenarios.
Visual assessment of GIC
With the electrojet located over the London region, GIC are reduced compared to the Northern Scotland electrojet location models, though are still large around the central UK on the eastern coast. From examining the differences between the models in this figure, it suggests that GIC primarily responds to the location of the electrojet, though there is some local variation due to regional conductivity differences (e.g. in the central region of Scotland in the AMK2003 model).
Figure 2 shows the locations of the 12 nodes with the largest average GIC for these particular scenarios and network topology. The nodes with the largest GIC are typically at the end of long lines or ‘corner’ nodes in the network but note that different nodes can become larger depending on the network model used. All chosen nodes record GIC values of over 80 A, with one over 225 A for the General Model with the electrojet across North Scotland (node B).
From Figure 4, it is clear that when the electrojet model is over London, there are still relatively large GIC in the central Scotland area. Equally, when the electrojet is located over northern Scotland, there are some nodes with significant GIC (>25 A) in the southerly parts of the UK. This suggests that the impact of the electrojet can be dispersed from the source region to elsewhere in the country via the high-voltage network.
The UK network is essentially composed of seven regions, as a consequence of the historic evolution of the grid. There are dense concentrations of nodes around population centres, with a series of long lines running between clusters of generators in central England and central Scotland. This allows currents to equalise over long distances from regions of high electric field to lower electric field over the high-voltage network. Thus, nodes in locations of low electric field may experience relatively large GIC, as they offer an easier route to normalization of current.
Analysis of variance
Attempting to visually analyse the GIC from all 504 electric field models is rather difficult. Indeed, we wish to understand the relative influence and importance of the four variables (2D conductivity model, electrojet position, 1D conductivity model and electrojet strength) in our simulations which most affects the size of GIC. Hence, we examine the relative effect of each variable on the GIC using analysis of variance (ANOVA) for all 695 nodes. As many of the nodes have relatively small GIC overall (<5 A), we also examine the 12 nodes with the largest average GIC. We are interested in finding general conclusions as well as checking for local or individual effects, so we plot the GIC values for each node in geographical form to look for regional variation.
- 1.
2D conductivity model, electrojet position, 1D conductivity model;
- 2.
2D conductivity model, 1D conductivity model, magnetic field strength;
- 3.
2D conductivity model, electrojet position, magnetic field strength;
- 4.
1D conductivity model, electrojet position, magnetic field strength.
From the F value at each node, the most important parameter was chosen as the one occurring most frequently in the above four combinations. For example, if electrojet position was the important variable from combinations 1, 3 and 4, while strength was the most important in combination 2, then the electrojet position has a dominant influence on the size of GIC generated at that particular node. Hence, it is recorded as the dominant parameter.
Frequency of the most influential variable for GIC
GIC ≤ 5A | Cond 2D | Ejet Pos. | Cond 1D | Strength | |
---|---|---|---|---|---|
All nodes | 25 | 69 | 432 | 32 | 137 |
Fixed ejet/strength ^{ a } | 27 | 180 | - | 488 | - |
Top 12 nodes | - | 2 | 6 | 3 | 1 |
Fixed ejet/strength ^{ a } | - | 3 | - | 9 | - |
The influence of the parameters on the 12 nodes with the largest GIC is examined in rows 3 and 4 of Table 3. Including all the parameters (row 3) shows the electrojet position which controls the size of GIC, while fixing the electrojet position and strength, as before, indicates that the 1D conductivity models are dominant. Note that if we do vary the fixed electrojet position (i.e. for the statistics in row 2), then the 1D conductivity remains the dominant factor.
Influence of conductivity models
We next examine the variation from the 1D and 2D models in the top 12 nodes, to determine which conductivity model has the largest influence. To do this, we plot the GIC values out as a series of ‘box’ plots. Box plots show the range of the data in the form of a central box giving the 25 to 75 percentiles, with whiskers extending to the 9 to 91 percentiles. The line in the middle of the box shows the median value. Note that if the median between models is not different at the 5% significance level, their notched intervals will overlap. For clarity, the outlier values are not shown in these plots.
Thus, at most nodes, the variation in GIC between the seven 1D models is larger than the variation between the three 2D models. Note that there are 168 values for each of the box plots in Figure 8, so the largest value outliers are not shown and the median and 9 to 91 percentile ranges will differ from Figure 7 which have only 72 values per box.
Discussion
The statistics from the analysis of variance method show that the electrojet position and strength are by far the dominant factors in the size of GIC values generated in the synthetic electric field models (c.f. Figure 5). Although this is not a new result, it does confirm previous findings and suggests that, in general, the conductivity structure is a second-order effect.
However, when examined in detail, it can be seen that in certain regions, variations in the 1D and 2D conductivity can enhance or diminish the GIC values particularly where the largest GIC are found. For example, the 2D AMK2003 model has a high conductivity structure in the central Scotland area, which gives lower GIC values than the other two models. In this area, the conductivity model is the dominant factor, leading to smaller GIC compared to the other models. The influence of the 2D conductivity models can be seen in Figure 6 where some of the nodes lie along more conductive lithologies in the southern part of the UK.
The 1D conductivity structure has a generally stronger influence and can lead to large differences in the GIC. In Figure 7, nodes D, E and G show much larger GIC when a homogeneous half-space value is used for the 1D conductivity, compared to the Southern Uplands model. In contrast, nodes K and L along the south coast are less sensitive to either 1D or 2D conductivity differences. Beggan et al. (2013) used the homogeneous half-space for their GIC analysis, and this has proven to be the most extreme form of 1D conductivity model.
Figure 3 shows that the most important surface variations occur on the boundaries of the conductivity contrasts, i.e. the coastline is obvious in many of the electric field models. As the UK is an island, this is the most important consideration for first-order modelling of GIC. The second-order differences are provided by the redistribution of the electric field by the variation within the 2D models, a feature noted in Beamish et al. (2002) for example.
Another point we wish to make is that even when the position of the electrojet is relatively distant, large GIC can occur. From Figure 4, it can be observed that when the electrojet is located over North Scotland, there are significant GIC along the coastal nodes in the east and west of the southern UK. This is likely to be a consequence of the topology of the UK network, whereby GIC outflows are dispersed from the source region along the least resistive parts of the high-voltage network.
We suggest further analysis should be made using measurements of GIC across the UK in key nodes when they become available. From such measurements, it is then possible to invert for conductivity (Vasseur and Weidelt 1977) and hence iteratively improve our knowledge of the conductivity structures affecting the nodes.
Conclusions
In this analysis, we are mainly concerned with identifying factors related to conductivity that may generate additional uncertainties in GIC which have not previously been accounted for. By examining three different 2D surface conductance models and seven different 1D conductivity depth models, we have attempted to assess some of the geologically feasible variations possible within the UK. We find that the major driver of GIC is the relative position and strength of the electrojet over the UK, while the influence from conductivity tends to be a second-order effect, in general, but can enhance or reduce local GIC in certain regions.
We have produced a series of 504 synthetic surface electric field scenarios for modelling GIC in the UK. The scenarios represent a best guess for various reasonable ‘worst-case’ scenarios during a large geomagnetic storm. The UK power grid is very well-connected and has a complicated topology giving it good resilience to the flow of large GIC. The multiple pathways through which currents can dissipate means that there are few nodes that are obviously vulnerable to major events, even given the uncertainties in our current modelling techniques.
Declarations
Acknowledgements
The author thanks Alan Thomson, Gemma Kelly and Andrew Richards for discussions and suggestions on improving the manuscript and National Grid UK for network data and parameters. I also acknowledge the thorough comments and suggestions from the two reviewers, whose help was crucial. This research was partly funded by NERC New Investigators grant NE/J004693/1 and from the European Community’s Seventh Framework Programme (FP7/2007-2013) under grant agreement 260330. This paper is published with the permission of the Executive Director of the British Geological Survey (NERC).
This is an Open Access article distributed under the terms of the Creative Commons Attribution License (http://creativecommons.org/licenses/by/4.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly credited.
Authors’ Affiliations
References
- Banks, RJ, Beamish D, Geake MJ (1983) Magnetic variation anomalies in northern England and southern Scotland. Nature 303: 516–518. doi:10.1038/303516a0.View ArticleGoogle Scholar
- Banks, RJ, Livelybrooks D, Jones P, Longstaff R (1996) Causes of high crustal conductivity beneath the Iapetus suture zone in Great Britain. Geophys J Int 124: 43–455. doi:10.1111/j.1365-246X.1996.tb07031.x.Google Scholar
- Beamish, D (2012) The 1:625k near-surface bedrock electrical conductivity map of the UK. Technical Report OR/12/037, British Geological Survey, pp 23. http://nora.nerc.ac.uk/20833/.
- Beamish, D, White J (2012) Mapping and predicting electrical conductivity variations across southern England using airborne electromagnetic data. Q J Eng Geol Hydrogeology 35: 99–110. doi:10.1144/1470-9236/11-026.View ArticleGoogle Scholar
- Beamish, D, Clark TDG, Clarke E, Thomson AWP (2002) Geomagnetically induced currents in the UK: geomagnetic variations and surface electric fields. J Atmos Terr Phys 64: 1779–1792.View ArticleGoogle Scholar
- Beggan, CD, Beamish D, Richards A, Kelly GS, Thomson AWP (2013) Prediction of extreme geomagnetically induced currents in the UK high-voltage network. Space Weather 11: 407–419. doi:10.1002/swe.20065.View ArticleGoogle Scholar
- Bernabeu, EE (2013) Modeling geomagnetically induced currents in dominion Virginia power using extreme 100-year geoelectric field scenarios - part 1. IEEE Trans Power Delivery 28: 516–523. doi:10.1109/TPWRD.2012.2224141.View ArticleGoogle Scholar
- Boteler, DH, Lackey AJC, Marti L, Shelemy S (2013) Power and Energy Society General Meeting (PES) In: Equivalent circuits for modelling geomagnetically induced currents from a neighbouring network, 1–5.. IEEE, New York.Google Scholar
- Cannon, P (2013) Extreme space weather: impacts on engineered systems and infrastructure. Technical report, Royal Academy of Engineering, London. ISBN 1-903496-95-0. www.raeng.org.uk/spaceweather.
- Lehtinen, M, Pirjola R (1985) Currents produced in earthed conductor networks by geomagnetically-induced electric fields. Ann Geophysicae4: 479–484.Google Scholar
- McKay, A (2003) Geoelectric fields and geomagnetically induced currents in the United Kingdom. PhD thesis, University of Edinburgh.Google Scholar
- Pirjola, R (2005) Effects of space weather on high-latitude ground systems. Adv Space Res 36(12): 2231–2240. doi:10.1016/j.asr.2003.04.074.View ArticleGoogle Scholar
- Pulkkinen, A, Bernabeu E, Eichner J, Beggan C, Thomson A (2012) Generation of 100-year geomagnetically induced current scenarios. Space Weather 10: 04003. doi:10.1029/2011SW000750.View ArticleGoogle Scholar
- Radasky, WA (2011) Overview of the impact of intense geomagnetic storms on the US high voltage power grid In: IEEE International Symposium on Electromagnetic Compatibility, 300–305.. IEEE Conference Publications, New York. doi:10.1109/ISEMC.2011.6038326.Google Scholar
- Schulte in den Bäumen, H, Moran D, Lenzen M, Cairns I, Steenge A (2014) How severe space weather can disrupt global supply chains. Nat Hazards Earth Syst Sci, 14: 2749–2759. doi:10.5194/nhessd-2-4463-2014.View ArticleGoogle Scholar
- Snedecor, GW, Cochran WG (1989) Statistical methods. 8th edn. Iowa State University Press, Iowa City.Google Scholar
- Thomson, AWP (2014) Geomagnetic observatories: monitoring the Earth’s magnetic and space weather environment. Weather 69(9): 234–237. doi:10.1002/wea.2329.View ArticleGoogle Scholar
- Thomson, AWP, Dawson EB, Reay SJ (2011) Quantifying extreme behaviour in geomagnetic activity. Space Weather 9: 10001. doi:10.1029/2011SW000696.View ArticleGoogle Scholar
- Thomson, AWP, McKay AJ, Clarke E, Reay SJ (2005) Surface electric fields and geomagnetically induced currents in the Scottish Power grid during the 30 October 2003 geomagnetic storm. Space Weather 3: 11002. doi:10.1029/2005SW000156.View ArticleGoogle Scholar
- Turnbull, K (2010) Modelling GIC in the UK. Astronomy & Geophysics 51(5): 25–26. doi:10.1111/j.1468-4004.2010.51525.x.View ArticleGoogle Scholar
- Turnbull, K (2011) Modelling of geomagnetically induced currents in the United Kingdom. PhD thesis, University of Lancaster.Google Scholar
- Vasseur, G, Weidelt P (1977) Bimodal electromagnetic induction in non-uniform thin sheets with an application to the northern Pyrenean induction anomaly. Geophys J R Astr Soc 51: 669–690.View ArticleGoogle Scholar
- Viljanen, A (2011) European project to improve models of geomagnetically induced currents. Space Weather 9: 07007. doi:10.1029/2011SW000680.View ArticleGoogle Scholar
- Viljanen, A, Pirjola R (1994) Geomagnetically induced currents in the Finnish high-voltage power system. Surveys Geophys 15(4): 383–408. doi:10.1007/BF00665999.View ArticleGoogle Scholar
- Viljanen, A, Pirjola R, Prácser E, Katkalov J, Wik M (2014) Geomagnetically induced currents in activity - modelled occurrence in a continent-wide power grid. J Space Weather Space Clim 4: 09. doi:10.1051/swsc/2014006.Google Scholar